View and Download Baxi Combi e installation and servicing instructions online. Gas Fired Wall Mounted Combination Boiler. Combi e Boiler pdf manual. Download Baxi Combi E manual. You have chosen to download this manual. Baxi Combi E, please click on the PDF link below. Boiler Manuals for the Baxi Combi E Instant appliance.
|Country:||Republic of Macedonia|
|Published (Last):||22 February 2008|
|PDF File Size:||1.14 Mb|
|ePub File Size:||13.35 Mb|
|Price:||Free* [*Free Regsitration Required]|
Boiler Manuals: Baxi Combi E Instant
Drain the primary circuit and undo the nut on the pressure gauge capillary. The appliance will run sufficiently cool without ventilation. Disconnect the discharge pipe from the 15e.
A small amount of water may drain from the boiler in the upright position. Short Parts List Set the temperature controls to maximum and the selector switch to the Off position Fig. When the new component has been fitted turn the selector switch fully anticlockwise against the spring pressure to Sensing position R and hold badi 2 seconds to reset the Tubes Remove the spring clips retaining the air box side baffle plates.
Remove the burner as described in Section Save to your online account What’s this? Don’t have an account?
Flame sensing electrode and lead connections 2. Disconnect the earth wire and pressure sensing pipe from the valve. Check that gas, water and electrical supplies are available at the boiler. Find the best energy tariff for you Get a quote. By-pass Pipe Diaphragm 2. Remove 1055e securing screws and hinge the facia panel down. Slacken the screws on the outlet sealing collar. Secure them with the screws previously removed Fig.
The flue terminal position must be in accordance with the current editions of B. bax
The preferred minimum gas pressure is Wall mounted powered flue condensing boiler gas fired central heating unit 8 pages. Lift the boiler using the lower edges. Part 2 Clause 4. Undo the screws securing the fan and hood to the appliance back panel. The Baxi Combi 80e and e can be fitted with flue systems as illustrated.
All delay timers mentioned in 3.
Baxi Combi 105E Instant
Existing energy customers Manage your energy Moving home. Drain the primary circuit and remove the socket head screws securing the pump head to the body and draw the head away. Unscrew and replace injectors as required Injector and examine the sealing gasket, replacing as necessary.
Withdraw the heat exchanger upwards and to the left of the gas valve, taking care not to damage any wires or controls. Slacken the facia securing screws and lift the outercase panel so that its locating tabs are clear of the facia.
Wall mounted powered flue condensing boiler gas fired central heating unit 48 pages. Control Box Cover 2. Hinge the facia panel upwards and refit the case front panel. Servicing The Boiler Technical Data – Combi e 4.
Central Heating Mode Fig. Save energy Energy saving tips. About us Contact us Emergencies. Page 19 Wall Plate 8. View your documents Cancel. Undo the screw on the pump wiring cover and remove the cover. This manual also for: Landlords Landlords cover Landlords repair Landlords insurance.
From the brass diverter manifold undo the nut on the heating flow pipe. For information on vertical flues consult the Baxi Combi Installer Guide or Notes for Guidance supplied with the vertical flue pack.