20S. 20S. E1FW. 1RA/ MF. CMP E1FW cable glands provide a flameproof seal on the cable inner bedding and in addition the gas tight seal has been tested to prove compatibility with. CMP Type E1FW Tri-Star Triple Certified Flameproof (Type ‘d’), Increased Safety ( Type ‘e’) and Restricted Breathing. (Type ‘nR’) cable gland for use in Zone 1.
|Country:||Sao Tome and Principe|
|Published (Last):||13 February 2004|
|PDF File Size:||4.60 Mb|
|ePub File Size:||15.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
CMP E1FW flameproof cable glands allow mechanical cable ee1fw and earth continuity via the cable armour termination. Dimensions shown are in millimetres unless otherwise stated.
CMP Glands – E1FW Ex Flameproof Cable Gland for Single Wire Armour (SWA) Cables
Cable Gland Weight Kgs. Available Entry Threads “C”.
Whilst continuing to push 1efw cable forward to maintain the armour in contact with the cone tighten the main item by hand until heavy resistance is achieved, then tighten a further full turn with a spanner. If required fit shroud over the cable outer sheath.
Cable Bedding Diameter “A”. Please Contact us for further details: Click for more info.
E1FW CABLE GLANDS, FLAMEPROOF E1FW ARMOURED CABLE GLANDS, FLAMEPROOF E1FW, CMP, HAZARDOUS AREA E1FW
On maximum size cables the clamping ring may only pass over the armour. Also the gas tight seal has been tested to prove compatibility with Restricted Breathing equipment. Deluge Proof version available, ferrule colour coded “white” for ease of identification. A detachable armour cone and CMP AnyWay clamping ring arrangement facilitates remote make off and enables the cable to be disconnected from the equipment.
Separate tightening actions for dmp inner displacement gland seal and the armour termination afford maximum control over the pressure applied to the cable bedding, and also allows the effectiveness of the gas tight seal to be tested.
Other thread forms, materials and finishes are available. This feature also allows the effectiveness of the gas tight seal to be tested. Remove a further 18mm of outer sheath to expose the armour.
Overall Cable Diameter “B”. The CMP E1FW Tri-Star Cable Gland is suitable for use with all forms of ckp area electrical equipment protection permitted in Zone 1, Zone 2, Zone 21 and Zone 22 provided always that the prevailing code of practice for selection and installation is observed, e. Remove a further 18mm maximum of outer sheath to expose the armour.
Ordering Reference Brass Metric. Twitter Updates New post: If you’re a human, don’t change the following field Enter your name: Tighten the main item by hand until heavy resistance is achieved, then tighten a further full turn with a spanner. Ingress Protection and Deluge Protection are essentially different and should not be confused with each r1fw.
E1FW | Ex e, Ex d, Ex nR, Ex ta, Explosive Atmosphere Cable Gland – CMP Products Limited
This completes the procedure for remote installation. Maximum control over the pressure applied to the cable bedding is achieved through separate tightening actions for the inner Displacement Seal and the Armour Termination. The CMP cable gland design is specified to contain an internal explosion and prevent transmission of sufficient energy to ignite a potentially flammable atmosphere outside the enclosure or junction box in hazardous areas.
This completes the procedure for the direct entry installation. Make an Enquiry Fill in this form to make an enquiry and our helpful team will be happy to provide a quote for this product or other www.
E1FW – Brass Flameproof/ Increased safety -Premium
This cable gland ensures a Flameproof seal on the cable inner bedding. The E1FW cable gland allows mechanical cable retention and earth continuity via the cable armour termination. This feature also enables the cable cmo be disconnected from the equipment.
Tighten the outer seal nut until either: Dimensions shown are in inches unless otherwise stated.